Get started with your BACnet Gateway and wireless I/O.
Setting your IP address to the correct range
The default IP of the Gateway is 192.168.0.100. Follow the video to set your computer’s IP address and access your new Gateway for the first time.
Connecting to your BACnet Gateway
Discovering WEMS wireless I/O and sensors
Editing your wireless sensors and I/O
Andy briefly touches on hopping between devices to increase wireless range.
From devices to BACnet objects
BACnet accumulators in action
Continuing on from teh previous video, Andy shows you a bit more on BACnet Accumulators and their usage with our wireless I/O and your BACnet IP BMS platform.
Deleting WEMS wireless devices and BACnet objects
In our final ‘Get Started’ video, we cover off how to delete points, BACnet objects or wireless devices in the correct manner. Removing them incorrectly can result in your devices being out of service and affecting the correct function of your control strategies built upon the wireless I/O.